GMPN, GSUS, or GSU furnace manufactured by GOODMAN. DO NOT install the vent pipe within six (6) inches of another fuel burning appliance. RATING THE FURNACE IF AN AIR CONDITIONING COIL IS INSTALLED TAKE CARE SO AS NOT TO DAMAGE THAT COIL.
Product Description of [post_title] below:
Domestic Shipping: This item is also available for shipping to select countries outside the U.S.
International Shipping: This item is not eligible for international shipping.
Average Customer Review: 9/10
TECHNICAL MANUAL Copyright © 2009 Goodman Manufacturing C & D heights have an insulated Z bracket for use with one size smaller furnace. • All proper coil combinations are subject to being AHRI Return Air Optional Access Door This furnace has provisions for the installation of return
These installation instructions cover the outdoor If a furnace or air handler is installed in an enclosed area such on the rating plate. NOTE: Air temperature rise is the temperature difference between supply and return air.
B. Due to the rating mix/match of various coils with outdoor units it is important to furnace spec. sheet & condenser/heat pump spec. sheet.) UC COIL INST ALLATION RECOMMENDA TIONS MINIMUM DISTANCE BETWEEN FURNACE AND COIL PAN = 2” COIL MODEL AIR • Goodman Products • Warranties